Model 9417DN: Vent fan has stopped working. Can I replace just the fan motor without replacing the whole unit? Bulb heater works.
Can I replace the fan motor without replacing the entire unit? Bulb heater works. Fan does not.
Thank you for your question on the model 9417DN. The replacement motor is available for this unit. Please contact our Customer Service Department at 888-336-3948 for assistance. Prior to contacting customer service, please check the data label on the unit for a possible suffix (-R01) or (-R02). This will assist them in determining the required part.
Date published: 2013-10-23
Vent & Heat operate together - Light separately
Figure for 9427P wiring option above shows connection to a single Dual Control switch. Can you provide instructions for connection to existing two switch junction box - switch for light and separate switch for vent & heat?
Our electrician was able to easily do this. Separate switch for heat and a a separate switch for fan with light. Works well and now 8 years old.
Date published: 2014-03-29
How close to the wall / cabinets can this be mounted?
When mounting this in the ceiling how far from the wall or cabinet faces does it need to be?
Thank you for your question on the model 9417DN single heat lamp/exhaust fan. It is recommended that you keep the 9417DN at least six inches away from a side wall or cabinet face. If you can keep it a foot away, that would be even better.
Date published: 2014-06-17
Install on 2 different circuits?
Is it possible to install the 9417DN on two different circuits, one for the vent and one for the light? If so, how would the neutral wires be connected? Remodeling a bathroom that never had a vent. Installing a new 20 amp circuit to the bathroom, but would like the vent to come on with the same switch that controls the existing light inside the shower that is on a 15 amp circuit. The heat lamp will be on the new 20 amp circuit controlled by a timer switch.
Thank you for your question on the model 9417DN single heat lamp bulb/exhaust fan. With the 9417DN only having a single white neutral wire and a thermal protector safety device, we would suggest using a single power source for both functions.
Date published: 2014-10-23
I have a 9417 heat-a-vent and the motor has failed. Can I purchase a replacement motor?
The motor is a Jakel brand, but has no part number. When plugged in, it turns CCW briefly and stops, but continues to hum.
Thank you for your question on the model 9417 single bulb radiant heat lamp/exhaust fan. The part number for the exhaust fan motor is 89224000 and it can be purchased through the “Shop for Parts” link at the top of our web site page.
Date published: 2014-04-07