4" to 3" adapter?
My ducting is 3". Is there an adapter that comes with it? Thank you!
No, you will have to change your duct to 4"
Date published: 2017-10-07
What motor speed and/or humidity sensor is compatible with ARN80L?
I wish to add motor speed control and a humidity-sensing on/off switch. Do you market such accessories? If not, could you tell me what type motor controller to use? I cannot tell from, reading your spec's whether or not this unit uses a capacitive-start motor (some controllers I have looked into specify not to use with capacitive-start motors).
Thank you for your question on model ARN80L exhaust fan/light. You can use a solid state speed control on the ARN80L (our model number is 57W). We also have two wall humidity sensors that can be used with the ARN80L (our model numbers DH100W and 82W). Please contact the Technical Service Department at 888-336-6151 if you need further assistance.
Date published: 2016-10-20
I am performing a retrofit and there is only 2 wires coming through, one gray and one orange with black stripe. The wires on the arn80l model are 2 sets of green white and black. Can i wire the fan and light to turn on from one switch and if so which wires go together?
Thank you for your question. Connect power cable to housing with appropriate UL approved connector. Connect black to black, white to white and green to green or bare wire. You must determine your “Hot” and your “Neutral” wires, and then you can wire them to a single switch. For further assistance, contact Nutone Technical Support at 888-336-6151.
Date published: 2018-01-22